Alarm Routed Non-Fire An A. Choosing the Devices parameter will bring up the Devices Walk Test screen Refer to Figure 2. This application is not suitable for separate transmission of sprinkler supervisory or trouble conditions. Install the door alignment tabs C in the unused Corner slots on the backbox top and bottom. The periodic detector test verifies the alarm operation of the detector. If Z1 activates, L1M1 will activate. If 9 or 15 is entered, the displayed value is 16.
. Once the equation evaluates True, it remains activated until a reset, even if the in- ternal equation becomes false. Formats are illustrated in Table 3. The power supply must have secondary power source i. Points transmitted may be programmed for a variety of types, including fire, water- flow, supervisory, etc.
All Systems Normal: During periods of no activity, the time field reflects the current time. No other system network functions can be implemented due to system contraints. The contact will open when power is removed. If no key is pressed during this minute, the function selected will be aborted and control will return to the state the panel was in prior to selection of that menu. Line 15 - The current time and date are displayed in this line. The total obtained in Table 3.
Otherwise, the tabs must not be broken. In addition, the wire gauge of a particular circuit is contingent on the length of that circuit. . In this ex- ample the door was mounted on the left, leaving the unused slots on the right. The user can change detector sensitivity values using this screen. Speed with limitless bandwith with only one click! This option inhibits the generation of a trouble message for Paper Out or Printer Off Line. Choosing the Zone parameter will bring up the Zone Walk Test screen.
When sufficient smoke is sensed, an alarm signal is initiated at the control panel. Program level change requires the master password, or a user password that allows access to the Program level. . General Zones The Duct Detector Zone is defined as a general zone used by one or more duct detectors, if duct detectors are being utilized in the system. To change the passwords, enter. Interior motion detectors should be placed on a separate supervisory circuit whenever possible, since they have a higher failure rate than other devices. Under this mode of operation each circuit operates in one of two stages: alert or evacuation.
If possible, these devices should all be of similar types. Turn off and remove all power sources. Autoprogram will not make a modification to the database for this point. Local Mode is programmed in the Local Parameters portion of System Programming. Zero indicates no schedule is applied, and occupied detector sensitivity values are used. The first 568 points transmitted may be programmed for a variety of types, including fire, waterflow, supervisory, etc. C h a n g e Terminal Status Y e s Line? For Left Corner right mounting, simply substitute right for left in the instructions.
This procedure places the center of the control panel keypad 60 inches 152 cm above the finished floor. If verification is not enabled for this point, the V indicator does not appear;. The internal relay is a latching-type relay to limit the isolator's power requirements. The drift compensation tolerance value has been exceeded. A short to any other system circuit will not cause communication loss. When the user presses the system test key the fire panel performs a chamber test of each intelligent detector to ensure its proper operation.
This key will appear only if a printer operation has been selected. In a domestic environment, this product may cause radio interference in which case the user may be required to take adequate measures. After proper authentication, the master password can be determined by deciphering the code. This may be the result of a burglary, other security violation, the failure of a device, an improperly addressed device, or failure of the field wiring. The 16th pin will remain on the outside of the board receptacle Figure 2. Zone Active a Minimum of 30 Sec.
Write down or memorize your passwords! Detailed information on the Alter Status options follows. This allows the operator to press a particular key until the desired character is displayed. A valid network node number range is 1-240. The screen will display the next loop when the last device on this loop is passed. This report may be sent to the Central Station for their records. For example, if 7 is entered, the displayed value will be 8. This module must not be activated in response to an alarm condition.
Below is an example of Zone 220 programmed as a reverse zone to activate zones on other network nodes. Enter a value of zero through ten. See chart on page 2 for compatible receivers. Disconnect all sources operate erratically or can be damaged when subjected to light- of power before servicing. Measure the voltage across the battery for a period of 20 hours. Take a fully charged battery and install the load resistor across the terminals.